Holz Rubber Application Data
To view the Holz Rubber Application Data Sheet Library, please click here.
Emergency Service with Time to Spare
Application: Expansion joints for a cooling tower at a natural gas power generation plant located the Southern United States.
Problem: A distributor was working with a power plant to provide expansion joints for their upcoming outage. About a month before the outage was to begin, the distributor learned that the expansion joints would not make it to the plant on time. The plant could not reschedule the planned outage, and that is when the distributor reached out to Holz Rubber Company due to a recommendation from the plant.
Solution: Because the project was time-sensitive, our engineering, production, and sales departments pulled together and established a time-line to have the joints built and delivered in an expedited manner. Our teams worked together and set an estimated ship date of 3-1/2 weeks; however, we were able to ship the entire order in just twelve days. The joints were delivered ahead of schedule, which allowed the plant to have the joints staged for the outage. The plant was able to complete the project within their scheduled outage. Our expedite service allowed the plant to get on-line and start producing power and revenue.
Saving Time and Money with a Fully Molded Flue Duct
Application: Refinery air supply line
Problem: A refinery reached out to a Holz Distributor to discuss concerns they had about one of their existing expansion joints. The joint looked like it was failing and they wanted to know if there was a better style of connection that they could use to prevent an unexpected blowout.
Solution: A Holz specialist reviewed drawings and photos of the application and determined the existing joint was a composite style that was not designed adequately for the system. The joint was installed with more material than necessary to be effective. The excess mate-rial caused overlapping of the joint and created weak spots due to abrasion fatigue. Our specialist recommended a 952“Arch Style”ultra-high movement expansion joint as an engineered solution that would eliminate the excess material and address offsets in the piping. This style would also save the refinery time and money with no need to re-align system components for installation. The ultra-high movement capability of the fully molded 952“Arch Style”expansion joint with fabric reinforcement helped eliminate the plants worry of downtime while providing long system life.
Vibrating Gravity Feed Piping
Application: Mechanical shaker at a pulp and paper mill carrying a mixture of ground cardboard and water.
Problem: A Holz Rubber Partner Distributor had a custom-er concerned about excessive vibration in their pulp piping system. The vibration was causing premature wear on adjacent components and had become a weak point in their process.
Solution: A Holz Expansion Joint Specialist developed a complete solution after reviewing the application, media, and environmental factors. They determined that a 945–W style expansion joint would absorb the vibration of the shaker to decrease the forces exerted on the system and prevent material build up. The 945-W style is designed to handle extreme movement and can alleviate the damaging vibration along the piping run. In order to install the expansion joint, removal of a section of pipe would be required and new flanges would be welded into place. Holz engineered and supplied a complete flue duct retrofit, consisting of the weld on flanges, expansion joint, retaining rings, and other hardware, making it possible for the plant to single source the entire project saving time and money.
Built In Offsets Extend Expected Life Of Flue Duct Expansion Joint
Application: Blower outlet at a Municipal Cogeneration power plant.
Problem: A power plant contacted Holz requesting help with one of their existing expansion joints. They had noticed that one of their duct joints was not lasting as long as other joints in similar applications.
Solution: A Our Inside Sales Specialist reached out to a local distributor and arranged for them travel to the plant to verify dimensional and application information. They found the ductwork was out of alignment and a large offset existed that had not been considered when the joint was last replaced. The distributor meticulously measured each flange and their proximity to each other and submitted the information to our Expansion Joint Engineering Department. We engineered a 942“U”style expansion joint with multiple built-in off-sets that it perfectly in the system and allowed the joint to perform in a relaxed state as designed.Holz Rubber Company is the industries leader when it comes to Engineering and Manufacturing fully molded Flue Duct Expansion joins.
Ultra High Movement Expansion Joint Engineered To Absorb Excessive Force
Application: FRP (Fiberglass Reinforced Pipe) rubber lined tailings chutes carrying various types of media over distance to a discharge hopper.
Problem: A Holz Partner Distributor was contacted by a facility that had FRP rubber lined chutes that were cracking and splitting. The fiberglass chutes are used through-out their tailings process. The chutes were showing signs of cracking at the flanges throughout the run, and it was separating at its connection to the discharge hopper.
Solution: A Holz Rubber expansion joint specialist reviewed all available information regarding application, media, and environment. They found that the movement of components throughout the system, combined with the flow of the media was causing stress and torque to the flanges beyond their specified capabilities. A Holz 952-2 double arch expansion joint with high movement capability was determined to be the best-engineered solution for the application. The Holz 952 design has a low enough spring rate that it would relieve the stress on the flanges by absorbing excessive forces in the system. This solution is sure to provide a longer chute life and less downtime for the end user.
Unforeseen Problems After Equipment Upgrade
Application: Industrial facilities are subject to constant and dynamic change. For a facility to run reliably, it must adapt to changes in processes, technology, and environmental requirements. These adaptations make it necessary from time to time to replace or reconfigure plant equipment.
Problem: A Customer came to Holz Rubber shortly after replacing their outdated boiler system and ductwork. They had an old expansion joint that had been part of the old boiler that was not a proper fit for the new ductwork. The breach opening between ducts was shorter than the original design,and the duct was misaligned, causing it to stretch axially and laterally. This misalignment was causing hotspots in the high temp joint material causing the maintenance personnel to doubt the joints’ ability to safely function.
Solution: A Holz Rubber expansion joint product specialist reviewed all of the information available for the entire system, focusing on the problem connection. Holz engineered a fully molded–945-S-W-style arch sleeve flue duct joint to meet the dimension, temperature and movement requirements of the system. When designing and installing any new equipment, it is essential to identify any potential problems in the entire system to ensure all of the components function safely and reliably based on their intended use.
Redesign Helps Power Plant Run Leak Free
Application: A72”water circulation system in a coal fired power plant.
Problem: Holz was contacted by a partner distributor that needed an engineered solution to re-place two circulating water expansion joints that had been in service since the1960s. The existing joints were unique since one side of each was vulcanized to the pipe instead of using flanges.
Solution: Our distributor and engineering team worked with the plant engineers to find a way to design joints with an industry standard. The decision was made to cut the pipe on the side that was vulcanized and replace them with standard ANSI flanges. This innovative solution made it possible for Holz to engineer 320 style EPDM joints with 150# integral flanges for easy and a cost savings installation.This solution is now in service and will keep the plant running leak free for many years.
Equipment Damage Causes Unscheduled Outage And Emergency Repairs
Application: It is crucial there is adequate airflow through-out a power plant to generate electricity. This air flow is created by industrial size fans that rotate at a very high velocity to move large volumes of air.
Problem: During normal operations at a combined cycle power plant one of these supply fans broke apart and caused a catastrophic damage to three different expansion joints. The force of the blades also destroyed ductwork and flow liners that were in the system If the equipment offline no power can be generated so the plant was eager to get the repair expedited. Additionally, the plant found they did not have adequate drawings on file, so the damaged equipment would need to be measured in place to produce new parts.
Solution: Working with a partner distributor, a Holz representative traveled to the site to measure and make recommendations to replace the damaged joints. The joints were found to be an odd size with a non-standard bolt pattern. The Holz engineering team was able to expedite the order in time to meet the deadline. The plant was able to get the unit back up and generating electricity and profits.
Overhead Leak Damages Expansion Joint
Application: Power plants use chemicals to produce steam, regulate temperature and, to keep the system free of corrosion. These chemical lines are running throughout each plant, and they typically have expansion joints installed to compensate for vibration and thermal fluctuations.
Problem: A distributor was concerned the cover (outer layer) of some of their expansion joints were delaminating. A Holz technical representative traveled to the plant with our distributor to troubleshoot.During the inspection, he found that the expansion joints had a layer of caustic on them from a leaking pipe overhead. The expansion joints did not have a cover that was chemically resistant; the joint was delaminating and cracking.
Solution: Holz’s engineering team made recommendations to help the customer fix this problem and to prevent it in the future. First, we recommended that the leak above be fixed before new expansion joints are installed. Second, we provided the new expansion joints with a Butyl cover that would protect the joints if they were ever exposed to the caustic chemical again. When expansion joints are part of any application, it is essential to consider the environment outside the joint as well as what will be flowing through it. Environmental factors such as chemical attack, UV, and abrasion by fasteners or other equipment should part of the design.
Incompatible Materials and Design Cause Failure at Potato Processing Facility
Application: Potato processing facilities manufacture many different products for human and animal consumption. Their processes use heat, steam, and oils to convert raw potatoes into products such as chips, flakes, and pellets. In these harsh conditions, expansion joint failures may occur if they are not built with materials that are compatible with the heat or chemicals they are ex-posed to.
Problem: Holz received a call from a distributor asking about the availability of an expansion joint that was needed in a hurry. They said that one of their customers re-placed a joint 48 hours earlier and it was already starting to fail. During inspection, the newly installed joint looked like it was delaminating and the rubber was softening due to heat or chemical attack. Also, the system was exposed to significant vacuum pressure that caused the joint to collapse.
Solution: Due to the high temperatures and chemicals in these conditions, Holz recommended their HRPL7 material as an ideal choice. The HRPL7 is rated for high temperatures in wet locations and is rated excellent for resistance to the chemicals used at this facility. At last report, the customer was very happy with the performance of this product and will use it in other applications in the future.
Engineering Solutions Helps Chemical Plant to Run Leak Free
Application: Air supply fan connection in a chemical plant.
Problem: A routine inspection a chemical plant found a tear in one of the expansion joints on their air handling system. Typically when an expansion joint tears it is a sign that the system has moved beyond the designed extension limit of the expansion joint. It is critical the system operates without leaking. The facility decided to replace the expansion joint immediately.
Solution: A Holz distributor who had been working with this facility contacted Holz to design a solution that would perform better than the current configuration. Holz developed a solution using their 945 style designed to al-low much more significant movement than the joint that had torn open. The 945 design is a fully molded expansion joint with a bellows in the body of the joint that allows maxi-mum movement without stressing the system. Our Engineered solution helped the plant to get running again and will ensure safe and leak-free operation.
Improvements in Expansion Joint Design Result in Fewer Leaks and a Safer Operation
Application: Dust cover for screener at a reduced iron plant.
Problem: In the process of making direct reduced iron the iron product is run through a device called a screener to help sort the product into various sizes. This is typically a very dusty process, and can include a great deal of vibration and abrasive media. Be-cause of these factors, the customer frequently had to replace or repair holes or tears in the existing seal that was wrapped and banded to the ductwork.
Solution: Our Engineering Group worked with our distributor to engineer a solution for this customer. We were able to design an expansion joint using our 942 style that was flexible enough to hold up to the vibration involved, yet strong enough to seal overtime by using abrasive resistant materials. The customer reports the joint is sealing and the end user is happy.
Adding an Expansion Joint Results In Reduced Noise and Equipment Damage
Application: A restaurant has a large exhaust fan that is used to re-move grease and other contaminants from inside the building where food is prepared.
Problem: This restaurant had problems with noise and vibration from their exhaust fan and contacted our distributor in the area to come up with a solution. When the exhaust ductwork was initially designed, the fan was connected directly to the building with a rigid metal duct. Because the duct is stiff, it was transfer-ring fan vibration directly to the restaurant causing damage and noise inside the building.
Solution: The distributor called Holz Rubber to help them design an expansion joint to install in the ductwork between the building and the exhaust fan. Our Engineering Group de-signed a sleeve type joint to install by banding it in place effortlessly. The solution worked by isolating the fan from the building to reduce vibration and the likelihood of equipment damage. Also, without the vibration traveling along the ductwork, there is a noticeable reduction of fan noise in the building.
Failed Expansion Joints Cause Unplanned Outages At Ethanol Plant
Application: In the process of making Ethanol, corn is pulverized and introduced into a slurry. This slurry travels through a series of tanks, pipes, and pumps before being reined into fuel.
Problem: An ethanol facility had many expansion joint failures in their corn slurry lines. Due to the fact the slurry runs at a high velocity and is abrasive, the original expansion joints were not designed correctly and didn’t last long enough fort he customer. The abrasive slurry was causing the inside of the existing joint to wear away and expose the nylon reinforcement, eventually causing the joint to fail. These failures caused costly unplanned shutdowns while the customer replaced joints and cleaned up the hazardous area around the failure.
Solution: Our Engineering Group worked with our distributor and the plant to create a design to enhance the reliability and function of the expansion joint. We did this by making two significant changes to the existing de-sign. The first was to include an abrasive resistant liner made from gum rubber, and the second was to change the arch style from wide open to a filled smooth bore to reduce turbulence.
Temperature Variables Make It Necessary To Have The Proper Fit
Application: The front and rear expansion joints on a gas turbine exhaust collector box in a facility owned by a large multi-national power company.
Problem: Temperature plays an important role in the success of a gas turbine operating efficiently. If the expansion joint is not installed correctly, or if it fails in service, gasses will leak into the GT enclosure. If the enclosure gets too hot it becomes less efficient and can cause a forced shut-down, eventually resulting in lost revenue.
Solution: The Holz Rubber Team supplied multi-layer, conical shaped high temperature flue ducts to back up the primary seals that tend to generate leakage. The new design has been successful for thousands of hours of operation, resulting in this product being implemented at other plant locations.
Compensating for Thermal Growth Extends System Life
Application: Connecting polypropylene strip line tanks for metal processing industries such as carbon steel, stainless steel, aluminum and exotic alloys.
Problem: A global supplier of polypropylene tanks was using conveyor belting bonded together to create the finished product. Quickly after install, the glue at the seams began to deteriorate causing the expansion joint to leak. The customer sent their drawings to three suppliers, the other two suppliers could not solve their problem. One of our knowledgeable sales team members took this opportunity to communicate with the customer providing them with engineering support, something they didn’t receive from previous suppliers.
Solution: The Holz Rubber Team supplied Chlorobutyl connectors with an extremely tight tolerance. In this application, our product has an estimated lifespan of between four and five years. Due to our high end quality and customer support, this company has been doing business exclusively with Holz for over five years.
High Temperature Ducting Joint Provides A Solution For A Gas Turbine
Application: Discharge of gas turbine engine bleed air to overboard ducting.
Problem: Gas turbines require testing for performance, emissions, and structural design integrity before being available on the market.
Solution: The Holz Team provided fully assembled expansion joint units for the testing of a new gas turbine. The gas turbine was tested successfully for use in simple cycle, combined cycle, and cogeneration applications. The turbine tested provides the highest power output of any aero derivative gas turbine generator package available on the market.
Adding A Teflon Gas Barrier To The Composite Joint Eliminates Premature Failure
Application: Ductwork between economizer and air heater, and PA ducts on a new 600MW lignite fired Circulating Fluidized Bed Boiler. Temps from 500° to 1100° F.
Problem: OEM expansion joints (fabricated by another company) consistently developed holes and leaks, even after repairs were made. The recently built plant went into un-planned outages several times to repair expansion joints.
Solution: The Holz Rubber Team provided replacement fabric expansion joints that were designed and constructed for the existing conditions, all while providing field support for the new installation at the customer’s request. The replacement fabric expansion joints solved the problems at the site and have allowed the customer to worry about more important things… like making money.
Holz Rubber Provides Quick Turnaround For Hydrogen Generation Plant Emergency
Application: Hydrogen Generation Plant.
Problem: The plant needed fully assembled fabric expansion joints for a hydrogen purification unit delivered in two weeks for installation.
Solution: With the help of our metal fabricators, we were able to ship all three fully assembled units consisting of belts, pillows, retaining bars, hardware, and frames in the two week time period ready for installation.
Holz Expansion Joint Allows Development of Catalysts to Improve Fuel Quality
High quality Catalysts improve refining process, producing better fuel quality and yields
Application: Catalyst manufacturing equipment at a Chemical Plant in Canada. The catalyst is used in a reβineries Fluid Catalytic Cracking (FCC) process to produce petroleum based products.
Problem: The existing expansion joint was not designed to compensate for the excessive lateral movement of the application, causing it to rip near the base of the βlanges. The rip exposed the expansion joints fabric reinforcement, which once exposed, can lead to catastrophic failure.
Solution: Holz engineered and manufactured a triple arch expansion joint designed specifically for the application, eliminating the possibility for catastrophic failure. Having a properly designed expansion joint for your application will decrease the possibility of unnecessary shut downs and potential safety concerns.
Custom Built Expansion Joints Solve Premature Failures Due to Piping Misalignment
Exceeding recommended misalignment causes multiple expansion joint failures costing down time and maintenance dollars.
Application: Piping to feed pipe on corn grinding mill at a dry grind ethanol facility. The dry grind ethanol facility produces fuel ethanol and Dried Distiller Grains (a low value animal feed product).
Problem: The process engineer was having difficulties identifying premature failures of the expansion joints on the grinding mills. Each expansion joint was failing after only 2 weeks of operation.
Solution: Holz Rubber Company determined the premature failure of the expansion joints was due to misalignment between the piping and the feed pipe on the grinding mill. Standard expansion joints are not designed to compensate for piping misalignment greater than 1/8”. Misalignment reduces the movement capabilities of the expansion joint and can severely reduce service life due to excess stress. Holz custom manufactured an expansion joint with a built in 3/4” lateral offset to account for the misalignment; keeping the plant running.
Custom Built Expansion Joint Eliminates Drip Tray Corrosion in Electro Polishing Process
Sulfuric acid solution causes drip tray corrosion, forcing early replacement and downtime.
Application: Electro polishing tanks are used to remove burrs and polish metal parts. The Electro Polishing tanks are used to polish fence posts at the largest fencing manufacturer and distributor in the Unites States.
Problem: The sulfuric acid solution used in the electro polishing process was dripping off the wire cathodes between the two tanks and destroying the drip trays. The tank operator needed a more permanent solution to contain the acid while also allowing the opening of the lids on the tanks.
Solution: Holz Rubber Company manufactured a custom three sided expansion joint to connect the two electro polishing tanks. The expansion joint contains the sulfuric acid solution and eliminates the need for drip trays that needed to be replaced often.
Coal Fired Power Plant Converted to one of the Cleanest Solid Fuel Plants in the Country
Strict Emission regulations met while salvaging local jobs.
Application: Wet Scrubber Inlet in a Bio Mass Plant. The plant utilizes the abundance of urban waste, scrap wood, and tree trimmings from the area to generate power for over 45,000 homes.
Problem: Their existing 1/4” thick Viton® expansion joint was tearing at the corners near the βlanges due to excessive movement of the duct system. The expansion joint in service was not designed to compensate for the 3” of concurrent movement in the system.
Solution: Holz Rubber Company, along with our local distributor visited the plant to evaluate the application. After the visit, Holz designed a 3/8” thick Viton® expansion joint with wire reinforcement to prevent tearing. More importantly, this expansion joint was designed to allow the excessive concurrent movements.
Torsional Misalignment On Bag Filter Flanges Causes Expansion Joint Failure
Proper piping alignment is critical to an Expansion Joints life cycle.
Application: The outlet to the bag βilter at Carbon Black Manufacturing Facility.
Problem: The existing βlanges were misaligned creating a twist in the expansion joint during installation. This twist caused material to fold over on itself creating hot spots which lead to premature failure. Additionally the existing expansion joint was not designed to handle the operating temperature.
Solution: Holz Rubber Company supplied a HRPL7 to handle the high temperature. The end user was instructed that they should align their piping to ensure a proper life cycle of the expansion joint. Unfortunately, the facility could not align their piping until the next outage. Since the plant could not modify the piping the Holz engineering team worked with the plant engineering team to come up with an installation method to eliminate the twist.
Adding a Full Cavity Pillow Eliminates Fly Ash Build-Up
Application: Air Heater Air Outlet on a lignite fired 600MW CFB Boiler.
Problem: Often the primary air pushed through the heater baskets on the air heater outlet is considered to be “clean”. In reality, there is fine particulate that clings to the baskets and as the primary air passes through, it pushes the dust into the ducts downstream.
The dust collects in behind the flow liner and eventually packs in tight enough to rupture expansion joints. The original OEM supplier failed to recognize the potential hazards for this application, and the joint became the cause of several forced outages.
Solution: Holz immediately recognized the problem and replaced the joint with a design that eliminated the collection of dust in the cavity by utilizing a design with a full cavity pillow. The plant has not experienced any further issues at this location.
Beefing Up The Composite Reinforcement With Aramid Eliminates Tearing
Application: A gas turbine air inlet at a power generation plant.
Problem: A power plant was struggling with a failing expansion joint. Cracks and tears close to the corners were causing a loss of air to the turbine during operation. This loss of air causes turbine efficiency related problems.
Solution: The Holz Team suggested replacing the existing fiberglass reinforced expansion joint with a new Aramid reinforced fabric expansion joint. This reinforcement is stronger and denser than the fiberglass and will provide for a longer service life in this application. The customer was pleased with the performance improvements and subsequently replaced the same expansion joint on the other turbines at the facility.
A Tabbed Pillow Eliminates Fly Ash Build-Up In The Sofa Duct
Application: Secondary Over-fire Air (SOFA) installed in a coal fired power plant where flue gas is typically 600°-700°F with some fly ash present.
Problem: Significant lateral movement is typical in this application due to boiler thermal growth. Flow liners experience large gaps and expose internal expansion joint components to turbulence and allows fly ash to collect.
Solution: Cold setting of ducts can reduce overall movements by half, which reduces the gap between liners under operating conditions. Mechanically fastening the pillow under the flanges forces “memory” into the pillow during thermal cycles of the boiler and keeps the components intact and operating as designed.